Wartsila’s User Group › Forums › 34 SG Wartsila Engine › Unitrol 1000 AVR’s Tagged: Unitrol 1000 AVR’s This topic contains 1 reply, has 2 voices, and was last updated by Jeremy Saar 2 months, 4 weeks ago. Viewing 2 posts - 1 through 2 (of 2 total) Author Posts June 21, 2018 at 6:56 pm #1880 TArnettKeymaster Hello. Are there any members (besides Plains End) that have Unitrol 1000 AVR’s installed on your generators? If so how are you meeting the NERC standard for PSS monitoring and reporting? June 22, 2018 at 8:05 pm #1881 Jeremy SaarParticipant On the AVR, scroll to setup and then scroll down to PSS. When you hit OK if PSS is active it will show PSS Active = True. You can either take a picture of that or log it. Author Posts Viewing 2 posts - 1 through 2 (of 2 total) You must be logged in to reply to this topic.