We have had success for several items by going to the vendor directly. One example is the HT/LT Heat Exchanger Water Pump Mechanical Seals. We had significant issues with leaking and found that the installed seals were not Nitrate resistant. We talked with the vendor and they made the Nitrate resistant seals and would sell direct. We have also speced out several O Rings and had them made locally.